ANSI/TIA/EIA Administration Standard for the. Telecommunications Infrastructure of. Commercial Buildings. Distributed by NDS INFORMATION- TELECOM. This guide is intended to be used as a reference to the application of the. ANSI/ TIA/EIA A Standard. It in no way reflects all the necessary infor-. ANSI TIA EIA – A Guide – English. ANSI / TIA / EIA – A Guide: Administration Standard for the Telecommunications Infrastructure of Commercial Buildings.
|Published (Last):||24 June 2006|
|PDF File Size:||9.51 Mb|
|ePub File Size:||12.91 Mb|
|Price:||Free* [*Free Regsitration Required]|
There is latitude within the standards to expand or vary implementation, apply more stringent criteria, and to specify organizational guidance on how these standards shall be applied and administered. A dedicated conduit will serve each outlet box.
They specify the absolute minimum acceptable requirements. These are the minimum initial planning requirements to design and build the appropriate infrastructure to support the foreseeable use of the intended facility. Space for connection of the building communication cable to the outside plant must be provided eka a separate room and not shared with other utility services, particularly the electrical service.
Libraries Libraries will be wired in accordance with the size of the room and need for fia.
Fire stops Approved UL fire stops must be used when penetrating fire rated walls or floors. In the case of proposed standards, the latest available draft shall be the controlling document.
Cable shall not be installed below ceiling in an exposed fashion, i. Each jack position on every wall plate is sequentially lettered A, B,left to right, then top to bottom.
This must be submitted in writing so that accurate infrastructure records can be maintained. Contact Us Departmental Support. If this is a design consideration, the number and location of communication outlets will be adjusted accordingly. Backbone cabling requirements The main building wiring closet will have single mode fiber originating from and distributed to each of the other wiring closets eeia each floor in the building.
Infrastructure Cabling and Wiring Standards
Each wiring run must be individually labeled. The volume of cable and predicted expansion determines the size and quantity of the ansk, conduit sor sleeved holes that make up the path.
When possible, this room will not be adjacent to the electrical distribution room. The list of codes and standards 2. Since 606q requirements are diverse, coordinate with the end user and Information Technology Services at the onset of design for renovation and new construction projects, and prior to the initiation of work orders, contracts, or other installation action for other types of projects.
All the information to label wall plates, horizontal cabling, patch panels and distribution frames fia be included in Information Technology Services cable management records system. Infrastructure Cabling and Wiring Standards.
Wireless access point installation locations shall be documented on plans. Cable trays and conduits must be properly grounded. The size of the cable path will be based on asni requirements of the facility. Pull strings The electrical contractor will provide a pull string in all empty conduits.
Where the standards appear to conflict with one another, the one with the most 606 requirements shall be applicable. Laboratories As a minimum, install one single wall phone outlet and one duplex data communication outlet. The recommended location for outlets is as follows: The wiring will be terminated with type blocks in the wiring closet.
Storage areas One wall-phone communication outlet for each fia over square feet and one additional phone outlet for each additional square feet are required. Note that room identifiers typically use the first character s position to specify floor s. Cables shall be secured at every corner.
Existing intra-building wiring There are currently five different types of legacy network infrastructure cabling that exists within campus buildings. Conduit specifications Conduits to communication outlets are to be a minimum of 660a inch. Fiber cabling from the first floor main wiring closet to and between each of the building floors shall be twelve strands 12 single-mode optical fiber. Cables shall be run in a qnsi fashion and shall not be woven among other utilities.
Information Technology Services maintains this documentation.
Infrastructure Cabling and Wiring Standards – Information Technology Services
All wiring must be removed all the way back to the cross-connect source. It is not all inclusive.
Cables shall not be tie-wrapped to or routed along electrical or gas conduit. All UTP cable and patch cordage shall be swept-tested through a prescribed frequency range. The A identifiers are shown in italics. Cable tray, conduit sor sleeved holes that provide this path are acceptable. Two categories of criteria are specified; mandatory and advisory. Contact Information Technology Services. This document provides required test values at specific discrete frequencies.
Installation and mitigation guidelines — Section 2: Residence halls Install one voice jack per room, one data jack per student, and one cable TV outlet in each room. These are mandatory data elements to be included in cable records systems. Faculty or staff offices Two duplex data communications outlets jacks for offices with fixed walls of square feet or more are required.
Removal of wiring Information Technology Services shall be consulted before removal of telephone wire and communications equipment, i. Graduate student offices One duplex communication outlet for every 75 square feet of space. All NEC codes for grounding of cable trays will be adhered to.